DBX1017FR Metal Dryer Vent Box
24 Gauge Powder Coated Metal Dryer Vent Box. The inexpensive DBX1017FR metal dryer vent box is powder coated white to match the washer box. The box is 10” WIDE BY 17″ TALL and designed to fit into a 2 x 6 framed wall. Designed and tested to meet 1 hour equal F&T fire rating requirement for through penetration fire rated system. * Please see installation instructions on how to meet 1 Hour requirement
The DBX1017FR also has the Length identification label inside it to meet the 2015 IMC building code requirement. IMC 504.8.5.
DBX1017FR (Dryer vent box)
The DBX1017FR’s are packaged 10 per carton
The DBX1017FR is 17’’ tall and 10’’ wide & 4 ¼ deep
The inexpensive DBX1017 FR is powder coated white to match the washer box. Designed and tested to meet 1 hour equal F& T fire rating requirement for through penetration fire rated system. The required length identification label that is attached inside the DBX1017FR saves you money and time. We are the only company who includes it while other companies charge you a few dollars for it separately.
Architects & Engineering:
- Click Here For ARCAT Specifications
- ARCAT BIM content
- Diagram- Wall DBX1017FR
- Product Specs- DBX1017FR
- DBX1017FR Submittal Form
- Mechanical Engineering Packet
- DBX1017FR QAI Test Metal Stud Load Bearing Fire Penetration Assembly Design Listing
- DBX1017FR QAI Test Metal Stud Non Load bearing Fire Penetration Assembly Design Listing
- DBX1017FR QAI Test Wood Stud Load Bearing Fire Penetration Assembly Design Listing
- DBX1017FR QAI Test Wood Stud Non Load Bearing Fire Penetration Assembly Design Listing
APPROVED FOR SINGLE AND MULTI-FAMILY CONSTRUCTION
THE DBX1017FR MEETS THE REQUIREMENTS FOR A 1 HOUR FIRESTOP SYSTEM FOR BOTH WOOD AND METAL FRAMED WALLS.
** see installation instructions
INTERNATIONAL MECHANICAL CODE
CLOTHES DRYER EXHUAST
SECTION 504.2 EXHAUST PENETRATIONS
Where a clothes dryer exhaust duct penetrates a wall or ceiling membrane, the annular space shall be sealed with noncombustible material, approved fire caulking or a noncombustible dryer exhaust duct wall receptacle.
This section requires the installer to provide a tag or label within 6′ of the dryer exhaust stating how many elbows and length of the dryer exhaust until it exits the residence.
CONSTRUCTION SOLUTIONS PROVIDES THE LABEL INSIDE THE DRYER VENT BOX AT NO COST TO MEET THE BUILDING CODE REQUIREMENT.